Customer called and said her furnace kept cutting off and not warming her house. We found the high limit switch tripping due to low airflow. After opening her system we discovered the blower wheel was clogged with debris preventing air from circulating through the furnace. We were able to remove the blower motor housing, clean and reinstalled the blower. Afterwards we got ther system operating properly. When you need help with your furnace or heat pump, Book Appointment with us.